G-TEC Torch Boosters must be installed by a person who is authorized to work on natural
TB-15 / 30/60 and 125 Torch Boosters connect to the building gas pipe with a G-TEC
provided 5’ flexible hose and ball valve.
TB-15 and TB-30 require a minimum 1/2” diameter low pressure gas supply pipe. TB-60
requires a minimum 3/4” supply pipe and TB-125 needs a 1” diameter supply pipe.
TB-15/30 and 60 use 120V 15 amp power; TB-125 uses 120V 20 amp power.
TB-250 and TB-500 Torch Boosters are hard piped with a minimum 1 1/2” diameter pipe
as close to the Booster as possible, then breaking down to a 3/4” pipe that is as
short as possible for final connection.
Both units can accept supply gas pressure between ¼ psi to 5 psi - higher pressure
inlet is possible by special assembly.
Both Torch Boosters use 208V single phase 30 amp electrical power.